John Maurice; South Paris, Maine wrote:
Question about gas furnace
short cycling and
heat anticipator setting
I am not sure why it would go off on high limit unless
you have a clogged filter. 200 degrees is plenty high for the high limit.
If it does cycle on high limit it should be no cause for concern.
Sometimes the gas companies change the btu content of the gas too. Check your thermostat under the cover is a little electric heater called the anticipator. its job is to cause the thermostat to turn off the burner before the temperature can over shoot. You will find them on forced air systems that use gas, oil or electric. Some hot water (hydronic) systems don't have them and most heat pump systems do not use them except for the backup heat function. Usually it is set to the current draw on the gas valve or oil primary. If it has been moved to a lower number that would cause the burner to short cycle. The way to know is to remove the cover on the thermostat and watch the mercury bulb to see if it is falling to the off position. If it is not check to see if the limit (shown below) is opening.
The correct way to set the anticipator is to measure the current draw of the gas valve/oil burner plus the heat assist device (show below) if it has one. If you have a clamp on ammeter wrap 10 (ten) turns of wire around the pick up and read the current and divide by 10. Ex: 6 amps =600MA or .6 amps. Set the scale on your thermostat to this number but don't be afraid to change it if you have too short or long a cycle.
WARNING: If you short circuit the gas valve terminals or oil burner W terminal you will burn out the heat anticipator. You will have to replace the thermostat! This is how a service person can sell you a new thermostat too.
This fan/limit has an "assist heater" the wires in the center. Which adds load to the heat anticipator and must be compensated for or short cycling of the valve or burner will result. If you do not see the wires in the center then you have a conventional control. The two wires you see in the center are connected across the gas valve in this system.
If your heat pump forms
ice outside in the heat mode click
If your air conditioner or heat pump ices up in the cooling mode click here.
If you have water leaking problems with your air conditioner click here to solve it.
For other heat pump problems click here.
For other heating system problems click here.
Any other questions feel free to contact us by any of the means below. good luck Scott.
This text written by: Scott Meenen * G & S Mechanical
Written By: Scott Meenen N3SJH of:
G&S MECHANICAL SERVICES.
Specializing in Mechanical, Controls and Electrical Modifications Of
Heating, Air-conditioning, Refrigeration, Cold storage,
Ice Production and Food preservation.
Anything having to do with Heat and Energy.
Serving MD, DC, and Northern VA.
Contact us by pager: 1-877-467-2914
Page us by e-mail email@example.com 240Chrs max.
Email us at: firstname.lastname@example.org